Refer the part-1 and part-2 of this water pipe sizing design calculation series before following this part of the piping system design calculation. In this part we will see how to calculate the maximum permissible pressure drop in the pipe system.

**What is pressure loss?**

The fluid, while flowing through the piping network, experience frictional resistance due to the velocity of the fluid and the viscosity of the fluid. This frictional resistance reduces the pressure of the fluid. This reduction of the fluid pressure is known as pressure drop or pressure loss of the fluid.

**Calculation of permissible pressure drop in a pipe**

*Maximum permissible pressure drop in a piping system = Total available head /Effective pipe length……Eq.1*

In part-2 of this series, we already calculated the effective pipe length for our example and the value of that is **22 meters**.

And, from the problem definition, it is clear that available pressure head for our case is **5 meters**.

So, from the Eq.1, maximum permissible pressure drop for the piping system for our example = **5/22=0.22 meter** of head per meter of pipe run.

In the next part (part-4), we will see how to calculate the hydraulic diameter of the piping network.

### Shibashis Ghosh

Disclaimer: I work for Altair. mechGuru.com is my personal blog. Although i have tried to put my neutral opinion while writing about different competitor's technologies, still i would like you to read the articles by keeping my background in mind.

#### Latest posts by Shibashis Ghosh (see all)

- INR 0.8 Million per Kg is the Cost of NOT Doing Design Optimization – How? - November 6, 2018
- How to Make Line Follower Robot without Using Microcontroller - September 15, 2018
- Design for Additive Manufacturing Worksheet - July 7, 2018