# Water Pipe Sizing Calculation Example – Part 2: Determining the Effective Pipe Length

Refer the Part-1 of this piping system design calculations series to know the problem statement and the assumptions.

What is Equivalent Pipe Length Method?

This the way of converting the Tee bends, valves and other pipe fittings in terms of equivalent pipe length. This value is added to the already existing pipe length to calculate the effective pipe length. So that the permissible pressure drop in the pipe can be expressed in terms of pressure drop per unit pipe length.

Calculation

Getting back to our pipe size calculation, we have 2 ball valves and 1 Tee bend apart from 7 meters of pipe line. And, also our initial assumption about the pipe diameter is 20 mm.

From the equivalent pipe length table it can be found out that

The equivalent length for the 20mm Tee bend = 1 meter

And, the equivalent length for the 20mm ball valve = 7 meter

So, the effective pipe length for our example= 1+7*2+7 meter = 22 meter

In the next part (Part-3) we will see how to calculate the permissible pressure loss using this effective pipe length value.

### Shibashis Ghosh

Hi, I am Shibashis, a blogger by passion and engineer by profession. I have written most of the articles for mechGuru.com. For more than a decades i am closely associated with the engineering design/manufacturing simulation technologies.
Disclaimer: I work for Altair. mechGuru.com is my personal blog. Although i have tried to put my neutral opinion while writing about different competitor's technologies, still i would like you to read the articles by keeping my background in mind.

#### Latest posts by Shibashis Ghosh (see all)

This site uses Akismet to reduce spam. Learn how your comment data is processed.