Refer the concept of the system resistance curve from my previous article for better understanding this article.

You will find an important equation there:

**Total system resistance = Frictional resistance + Resistance due to static head (height difference) + Resistance due to pressure head (pressure difference) + Resistance due to velocity (typically neglected)…………………Eq.1**

The above **Eq.1 **can be used for fan and pump system head curve calculation for the closed as well as the open systems. I already discussed how to draw a system performance or resistance curve for a closed system; I will discuss an example problem for an open system in this article.

**Example Problem for Plotting System Resistance Curve for an Open System**

Refer the schematics of the below open fluid handling piping system and plot the system resistance curve for the water system.

It has been found from calculation that the system exerts **50 ft** (water column) of frictional resistance head for a flow rate of **250 GPM.**

** **

**Solution:**

For solving the above problem, we have to use the **Eq.1. **Let’s try to find out the right hand side quantities of the Eq.1.

**Resistance due to static head = 4 ft **(the height difference between the suction and the discharge tank)

**Resistance due to pressure head **= **8 ft **(the pressure difference between the discharge and suction tank)

**Resistance due to velocity** =0 (negligible)

**Resistance due to friction @250 GPM flow rate= 50 ft **(Given)

**Two important piping or HVAC system fundamental rules to be remembered: **

*1.**The frictional resistance is proportional to the square of the flow rate.**2.**The values of the resistance due to static head and pressure head remain fixed with respect to the flow rate.*

The importance of the **rule-2 **is: we can use the same values for the resistance due to static head and pressure head for any flow rate while calculating the different data points.

**Data points calculations:**

**1. ****For flow rate = 250 GPM**

**Total system resistance =**50 ft (Frictional resistance given) + 4 ft (resistance due to static head) + 8 ft (resistance due to pressure head) =**62 ft**

** **

**2. ****For flow rate = 250*1.2=300 GPM**

**Total system resistance =**50 *1.2*1.2 ft (Frictional resistance using rule-1) + 4 ft (resistance due to static head) + 8 ft (resistance due to pressure head) =**84 ft**

** **

**3. ****For flow rate = 250*0.8=200 GPM**

**Total system resistance =**50 *0.8*0.8 ft (Frictional resistance using rule-1) + 4 ft (resistance due to static head) + 8 ft (resistance due to pressure head) =**44 ft**

** **

**4. ****For flow rate = 250*0.6=150 GPM**

**Total system resistance =**50 *0.6*0.6 ft (Frictional resistance using rule-1) + 4 ft (resistance due to static head) + 8 ft (resistance due to pressure head) =**30 ft**

** **

**5. ****For flow rate = 250*0.4=100 GPM**

**Total system resistance =**50 *0.4*0.4 ft (Frictional resistance using rule-1) + 4 ft (resistance due to static head) + 8 ft (resistance due to pressure head) =2**0 ft**

** **

**6. ****For flow rate = 250*0=0 GPM**

**Total system resistance =**50 *0*0 ft (Frictional resistance using rule-1) + 4 ft (resistance due to static head) + 8 ft (resistance due to pressure head) =12** ft**

** **

** **

Now, we are ready to plot the system resistance curve for the above six points (1 given + 5 derived) by putting the flow rate along the X axis and the total system resistance along the Y axis. The final system performance curve (pump system head curve to be precise) for open system looks like below:

I the next article I will discuss how to use system curve and pump curve for selecting suitable pump.

### Shibashis Ghosh

Disclaimer: I work for Altair. mechGuru.com is my personal blog. Although i have tried to put my neutral opinion while writing about different competitor's technologies, still i would like you to read the articles by keeping my background in mind.

#### Latest posts by Shibashis Ghosh (see all)

- INR 0.8 Million per Kg is the Cost of NOT Doing Design Optimization – How? - November 6, 2018
- How to Make Line Follower Robot without Using Microcontroller - September 15, 2018
- Design for Additive Manufacturing Worksheet - July 7, 2018

Too good man

man your site is really really informative and practically helpful